Sloan Royal Optima Plus Parts Breakdown and Troubleshooting Guide
Royal Optima Plus Breakdown PDF
Sensor flashes continuously only when user steps within range
A) Unit in start-up mode.
A) No problem. This feature is active for the first ten minutes of operation.
Valve doesn't flush; Sensor not picking up user
A) Range too short.
A) Increase the range.
Valve doesn't flush; Sensor picking up opposite wall or surface, or only flushes when someone walks by. Red Light flashes continuously for first ten minutes even with no one in front of the sensor
A) Range too long.
A) Shorten range.
Valve DOES NOT flush even after adjustment
A) Range adjustment potentiometer set at full "max" or full “min" setting.
A) Readjust potentiometer away from full “max" or “min" setting.
Unit flashes four quick times when user steps within range
A) Batteries low.
A) Replace batteries.
Valve DOES NOT Shut Off
A) By-pass orifice in diaphragm is clogged with dirt or debris, or by-pass is clogged by an invisible gelatinous film due to "overtreated" water.
A) Remove inside parts assembly and wash under running water. NOTE: size of orifice in by-pass is of utmost importance for the proper metering of water by the valve. Equiparts recommends that you do not enlarge or damage this orifice. Replace inside parts assembly if cleaning does not correct the problem.
Not enough water to fixture
A) Wrong Optima Plus model installed ( i.e. 1 GPF urinal installed on 3.5 gal closet fixture)
A) Replace with proper Optima Plus model.
Too much water to fixture
A) Control stop not adjusted properly.
A) Readjust control stop.
Men's Room Closet Bowls Un-Flushed
A) Closet being used as urinal.
A) Angle sensor slightly off fixture centerline to detect standing person in front of fixture.
High Vacuum Breaker installation unit not flushing. Elementary School Urinals NOT Flushing.
A) EBV-46-A beam deflector not installed.
A&B) Install EBV-46-A beam deflector to divert sensor beams.
Remove and then reinstall battery compartment door to activate 10 minute flashing range indicator feature. The range potentiometer is located at the top of the electronic sensor module beneath a rubber plug. Using the small screwdriver provided, turn the potentiometer a few degrees. Turn clockwise to increase range, turn counterclockwise to decrease range. Place cover over sensor module, position body into typical user range and check range by looking for red flashing light. Red light should only flash when picking up user. Repeat adjustment procedure until desired range is obtained. Reinstall optima plus. Refer to optima plus installation manual for greater detail on range adjustment procedures.
When Optima Plus has approximately 4000 flushes left, the same red light that appears at start-up will flash four times quickly whenever an object is detected. When this occurs, we recommend changing the batteries.
DO NOT use abrasive or chemical cleaners to clean the Optima Plus, they may dull the luster and attack the Plastic Cover and the chrome finish of the flushometer. Use only soap and water, then wipe dry with clean cloth or towel. While cleaning the bathroom tile, the Optima Plus should be protected from any spattering of cleaner. Acids and cleaning fluids can discolor or remove chrome plating.
Royal Optima Plus Troubleshooting PDF