Sloan Electronic Faucet Parts EAF-150 Parts Breakdown and Troubleshooting Guide
EAF-150 Breakdown PDF
- 1a. #80153 - EAF-10 - 2.2 GPM Aerator Spray Head
1b. #80757 - EAF-12 - 0.5 GPM Spray Head
1c. EAF-51 - 0.35 GPM Spray Head (Multi-Lam) - Call to Order
- 2a. #80758 - EAF-3-A - Throat Plate Assembly (Battery Models)
2b. #81297 - EAF-6-A - Throat Plate Assembly with i.q. Click (Battery Models)
- 3. #08747 - EAF-1000 - Battery Replacement Kit
- 4. #80154 - EAF-1 - Faucet Mounting Kit
- 5. #80759 - EAF-9 - Strainer (Filter)
- 6a. #80760 - EAF-1001 - Mixer Handle Assembly & Cartridge No Longer Available for Units Prior to 2004
#67555 - EAF-1022 - Mixer Handle Assembly and Cartridge Available for Units After 2004 - Call to Order
6b. #80155 - EAF-1002 - Handle Repair Kit
- 7. #84115 - EAF-1008 - 13" Flexible Supply Hose
- 8. #83827 - SFP-11 - Trim Plate for 4"
- 9. #81963 - SFP-22 - Trim Plate for 8"
- 10. #58426 - EAF-2 - Solenoid
- EAF-150 Complete Faucet Models: #57130, #57337, #58825.
Troubleshooting Q&ABelow is a Troubleshooting Q&A Guide for the EAF-150 Electronic Faucet from Sloan. The guide highlights the most commonly occurring problems and how to go about fixing them. As always you can call us for assistance or if you need to replace a part and/or unit.
Faucet does not function
A) Adhesive packaging label is still affixed over sensor eye. Remove adhesive label from sensor eye.
B) "Permanent Off" activated. Press button on faucet throat one time.
Water delivery is uncontrollable
A) Faucet is not working properly. This can happen for a variety of reasons. Knowing your particular circumstances will help us figure out if your dysfunctional faucet can be fixed, or if it needs to be replaced entirely. Please contact Equiparts at 800-442-6622 or view replacement EAF-150 complete faucets: #57130, #57337, #58825, #87168.
Faucet does not deliver any water when Sensor is activated
Solenoid valve produces an audible "CLICK"
A) Water supply stop(s) closed. Open water supply stop(s).
B) Water supply stop strainer(s) clogged. Clean water supply stop strainer(s).
Solenoid valve DOES NOT produces an audible "CLICK"
Faucet delivers very low flow / dribble
A) Water supply stop(s) may be partially closed. Open stop(s).
B) Water supply stop strainer(s) clogged. Remove, clean, and reinstall water supply stop strainer(s). Replace strainer(s) if required.
C) Aerator is clogged. Remove, clean, and reinstall aerator. Replace aerator if required.
D) Faucet is not working properly and may need to be replaced entirely. Call Equiparts and speak to a product expert for more help: 800-442-6622 or view replacement EAF-150 complete faucets: #57130, #57337, #58825, #87168.
Faucet continues to flow / dribble after user is no longer detected
i.q. - cliq doesn't function (-IC Models Only)
A) Button is not working properly. Please contact Equiparts for help finding a solution at 800-442-6622.
Water Temperature is too hot / cold on a faucet connected to hot / cold lines
A) Supply stops are not adjusted properly. Adjust supply stops.
B) For models with integral mixing valve – mixing valve is set improperly for the water temperature desired. Rotate mixing valve handle clockwise to decrease water temperature or counterclockwise to increase water temperature.
Care and Cleaning of Chrome and Special Finishes:
DO NOT use abrasive or chemical cleaners (including chlorine bleach) to clean faucets that may dull the luster and attack the chrome or special decorative finishes. Use ONLY mild soap and water, then wipe dry with clean cloth or towel. While cleaning the bathroom tile, protect the faucet from any splattering of cleaner. Acids and cleaning fluids will discolor or remove chrome plating.
EAF-150 Troubleshooting Guide PDF