Sloan Electronic Faucet Parts SF-2100, SF-2150, SF-2200, and SF-2250 Parts Breakdown and Troubleshooting Guide
SF-2100 / 2150 / 2200 / 2250 Breakdown PDF
- 1. #81793 - SFP6 - 110 VAC / 6 VDC Plug-In Adapter (US) (Models SF-2100 and SF-2200)
- 2. #32737 - UNCEN91 - 4 AA Batteries (All Models)
- 3a. #81114 - SFP40A - Control Module with Adjustable Button (6 pin connector)
3b. #80298 - SFP8 - Control Module (Old Style 4 pin connector)
- 4. #86194 - SFP10 - Flex Hose, Control Module to Spout (All Models)
- 5. #83827 - SFP11 - 4" Trim Plate with Spacer (All Models)
- 6a. #83568 - SFP41A - Sensor Assembly (6 pin connector)
6b. #86195 - SFP34 - Sensor Assembly (Old Style 4 pin connector)
- 7. #56794 - ETF617A - 3/8" Bak-Check® Tee Compression Fitting
- 8. #86196 - SFP15 - Strainer (located in water inlet of control module)
Troubleshooting Q&ABelow is a Troubleshooting Q&A Guide for the SF-2100, SF-2150, SF-2200, SF-2250 Electronic Faucets from Sloan. The guide highlights the most commonly occurring problems and how to go about fixing them. As always you can call us for assistance or if you need to replace a part and/or unit.
Delivery of water is uncontrollable
A) Faucet is not working properly.
Faucet does not deliver any water when sensor is activated
Solenoid valve produces audible "CLICK."
A) Water supply stop(s) closed. Open supply stop(s) completely.
B) Water strainer in control module is clogged. Close supply stops and remove water inlet line at control module. Remove clean and reinstall strainer and water inlet line. Replace strainer if required.
Solenoid valve DOESN'T produce audible "CLICK"
A) Batteries low (battery powered models). Replace batteries.
B) Power failure (transformer powered models). Check power supply.
Faucet delivers only a slow flow or dribble when sensor is activated
A) Water supply stop(s) may be partially closed. Open stop(s).
B) Water strainer in control module is clogged. Close supply stops and remove water inlet line at control module. Remove, clean and reinstall strainer and water inlet line. Replace strainer if required.
C) Aerator is clogged. Remove, clean, and reinstall aerator. Replace aerator if required.
D) Faucet is not working properly.
Faucet doesn't stop delivering water or continues to drip after user is no longer being detected
A) Solenoid Valve is not working properly.
The water temperature is too hot / cold on a faucet connected to hot / cold supply lines
A) Supply Stops are not adjusted properly. Adjust Supply Stops.
Care and Cleaning of Chrome and Special Finishes:
DO NOT use abrasive or chemical cleaners to clean flushometers as they may dull the luster and attack the chrome or special decorative finishes. Use ONLY mild soap and water, then wipe dry with clean cloth or towel. While cleaning the bathroom tile, the flushometer should be protected from any splattering of cleaner. Acids and cleaning fluids can discolor or remove the chrome plating.
SF-2100 / 2150 / 2200 / 2250 Troubleshooting Guide PDF
View the Sloan SF-2100 / 2150 / 2200 / 2250 repair parts or our selection of Sloan electronic faucets.