Sloan Electronic Faucet Parts SF-2100, SF-2150, SF-2200, and SF-2250 Parts Breakdown and Troubleshooting Guide
Delivery of water is uncontrollable
A) Faucet is not working properly. Please contact Equiparts at 800-442-6622
Faucet does not deliver any water when Sensor is activated
Solenoid valve produces audible "CLICK."
A) Water supply stop(s) closed. Open supply stop(s) completely.
Solenoid valve DOESN'T produce audible "CLICK"
A) Batteries low (battery powered models). Replace batteries.
Faucet delivers only a slow flow or dribble when sensor is activated
A) Water supply stop(s) may be partially closed. Open stop(s).
Faucet doesn't stop delivering water or continues to drip after user is no longer being detected
A) Solenoid Valve is not working properly. Please Contact Equiparts at 800-442-6622
The water temperature is too hot / cold on a faucet connected to hot / cold supply lines
A) Supply Stops are not adjusted properly. Adjust Supply Stops.
DO NOT use abrasive or chemical cleaners to clean flushometers as they may dull the luster and attack the chrome or special decorative finishes. Use ONLY mild soap and water, then wipe dry with clean cloth or towel. While cleaning the bathroom tile, the flushometer should be protected from any splattering of cleaner. Acids and cleaning fluids can discolor or remove the chrome plating.
SF-2100 / 2150 / 2200 / 2250 Troubleshooting Guide PDF