Sloan GEM 2 Parts Breakdown and Troubleshooting Guide
GEM 2 Breakdown PDF
Important: The GEM Flushometer is engineered for quiet operation. Excessive water flow creates noise, while too little water flow may not satisfy the needs of the fixture. Proper adjustment is made when plumbing fixtures is cleansed after each flush without splashing water out from the lip AND a quiet flushing cycle is achieved. Never open Control Stop to where the flow from the valve exceeds the flow capability of the fixture. In the event of a valve failure, the fixture must be able to accommodate a continuous flow from the valve.
Attention Installers: With the exception of the control stop inlet, DO NO USE pipe sealant or plumbing grease on any valve component or coupling! To protect the chrome or special finish of Sloan Flushometers, DO NOT USE toothed tools to install or service these valves. Use our A-50 Super Wrench or other smooth-jawed wrench to secure couplings. Regulations for low consumption fixtures (1.6 GPF closets and 1.0 GPF urinals) prohibit use of higher flush volumes.
Valve does not function
A) Control stop or main valve is closed.
B) Handle assembly is worn.
C) Relief valve is worn and sticking in UP position
A) Open control stop or main valve.
B) Install Sloan handle repair kit G-50-A or replace handle.
C) Replace piston.
Insufficient volume of water to adequately siphon fixture
A) Control stop not open enough
B) Urinal piston parts inside a closet valve
C) Low-Consumption valve installed on a non-low consumption fixture
D) Inadequate volume or pressure at supply
A) Adjust control stop for desired delivery of water
B) Replace piston parts with proper closet piston
C) Replace with proper piston kit
D) Increase water pressure or supply (flow) to valve. Call Equiparts for assistance at 800-442-6622.
Length of flush too short, or valve closes off immediately
A) Piston assembly us not hand-tight.
B) Enlarged bypass orifice from corrosion or damage.
C) Urinal piston in closet flushometer.
D) Low-consumption piston installed in non-low consumption fixture.
E) Handle assembly worn.
A) Screw the assembly hand-tight.
B) Instal new inside parts kit to correct problem and update flushometer.
C) Replace piston with proper closet piston.
D) Replace with proper piston kit.
E) Install Sloan handle repair kit G-50-A
Length of flush too long or fails to close off
A) Piston is not seating properly, bypass orifice is clogged because of foreign material, or bypass orifice is clogged by an invisible gelatinous film from "over-treated" water.
A) Disassemble the working parts and wash thoroughly. Note: size of the orifice in the bypass is of utmost importance in the proper metering of water into the upper chamber of the valve. DO NOT enlarge or damage this orifice. Replace piston if cleaning does not correct problem.
Leaking at handle assembly
A) The B-39 seal may have deteriorated
B) Handle Gasket has been omitted
C) Valve handle bushing is worn
A) Install new B-39 seal. Note: The B-85 seal will easily slide onto the bushing if it is wet.
B) Install G-35 handle gasket or Sloan handle repair kit G-50-A
C) Install Sloan handle repair kit G-50-A, or replace handle
GEM 2 TroubleShooting PDF